Projects per year
Partial discharge (PD) is measured simultaneously using free-space radiometric (FSR) and a galvanic contact measurement technique based on the IEC 60270 standard. The PD source is an emulator of the floating-electrode type. The radiated signal is captured using a biconical antenna. A method of estimating absolute partial discharge (PD) activity level from a radiometric measurement by relating effective radiated power to PD intensity using a PD calibration device is presented.
|Title of host publication||2016 URSI Asia-Pacific Radio Science Conference, URSI AP-RASC 2016|
|Publisher||Institute of Electrical and Electronics Engineers Inc.|
|Number of pages||4|
|Publication status||Published - 20 Oct 2016|
|Event||2016 URSI Asia-Pacific Radio Science Conference - Grand Hilton Seoul Hotel, Seoul, Korea, Republic of|
Duration: 21 Aug 2016 → 25 Aug 2016
https://www.ursi.org/content/AP-RASC/AP-RASC2016/URSI_AP-RASC_2016_Program.pdf (Link to Conference Programme )
|Conference||2016 URSI Asia-Pacific Radio Science Conference|
|Abbreviated title||URSI AP-RASC 2016|
|Country||Korea, Republic of|
|Period||21/08/16 → 25/08/16|
FingerprintDive into the research topics of 'Assessment of absolute partial discharge intensity from a free-space radiometric measurement'. Together they form a unique fingerprint.
- 1 Finished
Scalable Non-invasive Radiometric Wireless Sensor Network for Partial Discharge Monitoring in the Future Smart Grid
Glover, I., Atkinson, R., Soraghan, J., Judd, M. & Vieira, M. D. F. Q.
1/04/13 → 1/04/18